Last update: Jan 13, 2017
Most flue gases produced by the combustion of fuels contain contaminants that can condense into sulfuric, sulfurous, or hydrochloric acid droplets. Flue Gas Dew Point Corrosion occurs when these aggressive acids condense on carbon and stainless steels in convection sections, flue ducts, and stacks. The amount of contaminants in the fuel is directly correlated with the concentration of the acid droplets, and therefore with the degree of corrosion.
There are several ways in which flue gas dew point corrosion can be avoided. More resistant materials can be used in the construction of flues, which can prevent corrosion. Also, limiting the number contaminants in heater and boiler fuels is another good way to prevent corrosion from occurring. Although, it should be noted that the latter method is far more difficult to accomplish, since most fuels contain sulfur compounds and some are contaminated with chlorides. Another way to prevent corrosion is to maintain the surface metal temperatures of exposed equipment above the dew point. Finally it is possible to protect cooler surfaces by applying a coating that is resistant to the acidic condensate and will withstand the temperatures to which it is exposed.
Recommend changes or revisions to this definition.
May/June 2005 Inspectioneering Journal
By John Reynolds at Intertek
Most all flue gases produced by the combustion of fuels contain contaminants that can condense into acid droplets. The amount of contaminants will determine the concentration of the acid droplets.
If you are developing a mechanical integrity program, or you would like to optimize your existing mechanical integrity program, do you have qualified MI consultants to meet your regulatory needs? If you already have a sound, defensible MI inspection system in place, do you have qualified and experienced personnel maintaining your program?